Rules you must follow, who’s responsible and when to notify the Environment Agency.
You must follow these rules if you store silage, slurry or agricultural fuel oil.
You need to know the general rules that apply if you store any of the 3 substances, as well as specific rules for storing and handling each one.
You’re responsible for making sure you meet the rules if you control, manage or look after a farm or an installation on a property, eg as a:
- farmer or land manager
- tenant farmer - unless you can prove someone else, eg the leaseholder, is jointly or wholly responsible
You can be prosecuted and fined up to £5,000 in a magistrates’ court, or get an unlimited fine in the Crown Court, if you don’t follow the rules and take care to avoid causing pollution.
New storage and substantial changes
A new or substantially changed store must:
- follow the specific rules for the substance you’re storing
- have an expected lifespan of at least 20 years with maintenance (any part of a silage effluent tank that’s underground must last 20 years without maintenance)
- be at least 10 metres clear of inland or coastal waters - you may need a larger ‘safety zone’ in some cases, eg near a water supply intake
Although your store itself must be at least 10 metres clear of inland or coastal waters, drains and sealed pipes can be within 10 metres of these features if the Environment Agency agrees an exception. Ask for an exception when you tell the Environment Agency about your project.
‘Substantial changes’ usually means structural alterations, rather than minor repairs. Check with the Environment Agency if you’re unsure.
If your installation was built before March 1991, or a contract for construction was entered into before March 1991 and completed before September 1991, it’s exempt from the rules for new stores. However, if you make substantial changes - eg structural changes, increasing capacity or relocating - your store is no longer exempt.
The Environment Agency can also serve a notice at any time requiring you to bring storage up to the current standards if it believes there’s a significant risk of pollution.
Before you start work
It’s up to you to decide what planning and work is needed but you must:
- tell the Environment Agency at least 14 days before you begin construction - you can also contact them for advice on planning and building a store
- make sure you don’t pollute the surrounding environment - eg rivers or other watercourses
- check if you also need planning permission
Once your storage is built you must carry out maintenance to make sure there’s no risk of pollution.
Tell the Environment Agency
You must notify the Environment Agency at least 14 days before you build new storage for silage, slurry or agricultural fuel oil, or make substantial changes to an existing store.
You must also tell the Environment Agency if you intend to make or store field silage or non-baled bags - there are specific rules and a form.
Contact your local office
Call or write to your local Environment Agency office.
- your name, address, telephone number and email address
- the type of store you’re proposing to build or change
- the exact location of the site (8-figure grid reference)
You’ll need to supply the following when you contact the Environment Agency so they can assess your proposal:
- a site plan drawing of the structure
- a design drawing confirming the materials that will be used and their design, specification and layout - you may also be asked to confirm that your design meets the requirements of BS 5502
- if you plan to use prefabricated products, a copy of the manufacturer’s specifications and guarantee
- if the structure is constructed from earth, analysis about the soil type, depth and permeability and a description of how it will be engineered
- for underground or partially underground silage effluent tanks you’ll need a certification from the installer - you must provide this certification to the Environment Agency because the tank is required to perform for at least 20 years without maintenance.
You’ll usually get a written assessment of your proposal that says whether its been approved or not. The Environment Agency may contact you, rather than giving you a written assessment, to give you guidance on changes you need to make to your installation before it can be approved.
There are specific rules for making and storing silage.
The rules don’t apply to silage you store temporarily in a container or trailer for transportation.
Where to store silage
You must not make or store any silage, or unwrap baled silage, within 10 metres of inland or coastal waters.
In addition you must not store field silage within 50 metres of a ‘protected water supply source’. This is any place where water is abstracted (taken) for any of the following purposes:
- human consumption
- use in farm dairies
- human food preparation
All parts of a silo must be resistant to attack. Your silo must have:
- an impermeable base extending beyond any walls
- impermeable drainage collection channels around the outside, flowing into an effluent tank
The base must comply with:
- British Standard 8007:1987 and British Standard 8110-1:1997 (for concrete bases)
- British Standard 594/EN 13108-4:2006 (for hot-rolled asphalt bases)
If your silo has walls they must withstand wall loadings set in British Standard 5502-22:2003+A1:2013..
Ask your manufacturer, or check the mannual that came with your equipment, to find out if it meets these British Standards.
Your silo must have an effluent collection system.
If all parts of an effluent tank are above ground, the tank must be constructed to resist attack from silage effluent for at least 20 years with maintenance. If any part is below ground it should be impermeable for at least 20 years without maintenance. You’ll be asked to prove your tank is suitable, eg with a manufacturer’s guarantee.
You can store silage effluent and slurry together if your tank has enough capacity and is built to withstand both types of effluent. However, mixing slurry can give off gases that are lethal to humans and livestock, and you must never put silage effluent into an under-floor slurry store.
The minimum capacity rules for effluent tanks should give you at least 2 days’ storage at peak flow. However, it’s up to you to ensure you’ve enough capacity to avoid the risk of pollution.
|Silo capacity||Minimum effluent tank capacity|
|Up to 1,500 cubic metres||20 litres for each cubic metre|
|Over 1,500 cubic metres||30 cubic metres, plus 6.7 litres for each cubic metre of silo capacity over 1,500 cubic metres|
Baled silage must be sealed in an impermeable membrane or bagged. It doesn’t need a specially constructed base but you must make sure any silage stored directly on the ground can’t leak into a water source.
Baled silage must be kept at least 10 metres clear of inland or coastal waters.
Field silage and non-baled bags
For silage to be stored as ‘field silage’ there must be no construction works, eg walls or earth banks, and topsoil must not be disturbed.
If you make field silage or non-baled bags you must:
- choose a suitable site - eg if you store silage in a non-baled bag in your farmyard you must make sure you can contain any drainage
- notify your local Environment Agency office at least 14 days before you first use the site
Notify the Environment Agency
Send the completed form to your local Environment Office.
There are specific rules when you make and store slurry, including in earth-banked stores.
Run-off from solid manure stores, woodchip, or straw-bedded corrals or stand-off pads counts as slurry. You must collect and store it either separately or in your main slurry store.
The rules don’t apply to slurry you store temporarily in a container or trailer for transportation.
Where to store slurry
You must not site slurry storage tanks, effluent tanks, channels or reception pits within 10 metres of inland or coastal waters without written agreement from the Environment Agency.
All slurry stores
Slurry tanks, reception pits, pipes and channels must be impermeable and meet the anti-corrosion standards set in British Standard 5502-50:1993+A2:2010. They should last for at least 20 years with maintenance.
The base and walls of your slurry tank and any reception pit must withstand the wall loadings set in the standard.
You’re responsible for making sure your storage and maintenance complies with the rules - get professional advice if you need it.
When calculating the required capacity of your steel or concrete store you’ll need to include a minimum of 300 millimetres of freeboard. For earth-banked stores you’ll need a minimum of 750 millimetres, and you must maintain this freeboard during use. Freeboard is the vertical distance between the crest of your tank or lagoon and the slurry surface.
You’ll normally need capacity for at least 4 months’ slurry storage. What this means for you will depend on how much slurry you use, the size of your tanks and expected rainfall. Software available from Planet can help you work out your average rainfall.
If you’re in an area with above average rainfall you’ll need more capacity. Speak to the Environment Agency or a consultant if you’re unsure how much you’ll need.
If you operate with less than 4 months’ capacity the Environment Agency may refuse your proposal or ask you to prove that it’s sufficient and to explain the steps you’ve taken to protect the environment.
Any temporary storage facilities you have - eg a reception pit - must be large enough to store a minimum of 2 days’ combined slurry production and likely rainfall.
If your slurry tank, effluent tank or reception pit is fitted with a drainage pipe it must have 2 valves separated by a least 1 metre. Each valve must be able to shut off the flow of slurry and be locked when not in use.
The exception to this rule is if your slurry storage tank drains through the pipe into another tank at the same level, or of equal or greater capacity.
Earth-banked slurry stores
An earth-banked store must have impermeable soil to a thickness of at least 1 metre. You may need laboratory analysis and confirmation from a civil engineer to be sure your soil is suitable. Alternatively you can import impermeable soil or use a synthetic liner.
The base of a weeping-wall store must extend beyond its walls and include perimeter drains to catch escaped slurry and drain into an effluent tank.
Your irrigation system must not deposit slurry within 10 metres of inland freshwater or 50 metres of any water supply. You must assess the risk of direct run-off from land you intend to irrigate, and identify unsuitable areas.
Agricultural fuel oil
You must follow these rules if you both:
- build a new agricultural fuel oil store or make substantial changes to an existing one
- store over 1,500 litres of agricultural fuel oil on your farm
Other rules may apply if you store fuel oil:
- for domestic purposes
- for another business you run from your farm
- in a tanker temporarily for transportation on roads or around your farm
- in mobile browsers or drums temporarily stored alongside mobile plant
Wherever fuel oil is stored on your land you’re responsible for taking precautions to prevent and contain spillages - eg by fitting an alarm to alert you to overfilling.
Where to store fuel oil
You can store fuel oil in one location or spread across your farm. It must be stored in a tank or drum that meets ISO 9000. (Check the mannual that came with your tank or drum, or ask the manufacturer.)
No part of your installation can be within 10 metres of inland or coastal waters - including yard drains, dry ditches and land drains.
If tanks are underground they must also follow the Defra Groundwater Protection Code.
A tank or drum must be surrounded by a secondary containment structure or ‘bund’.
The bund must:
- have a life-expectancy of at least 20 years with maintenance
- be impermeable to oil and water (walls and base), with no drain-down pipe
- contain every part of the tank, with taps and valves directed down and locked shut when not in use
- contain delivery pipes that are permanently attached to the primary tank, which must be fitted with self-closing taps or valves and locked inside when not in use
If you buy a combined storage tank and bund system you must make sure it will meet the regulations when in use.
You must dispose of any waste fuel oil or mix of oil and water that collects in the bund without causing pollution.
The required capacity of a bund depends on your type of storage.
|Type of storage||Minimum capacity of bund|
|Single tank||110% capacity of the tank|
|Multiple tanks||110% of the capacity of the largest tank or 25% of the total volume that could be stored in all tanks in the area - whichever is greater|
|Other storage - eg drum||At least 25% of the total volume that could be stored at any time|
If you’re served a notice
The Environment Agency can ‘serve a notice’ to stop you using an unsuitable silage, slurry or agricultural fuel oil store until it’s improved or relocated. They’ll do this if they think there’s a significant risk of pollution - eg if you’ve not allowed enough capacity to store slurry.
You’ll have at least 28 days to carry out the work. You may be allowed more time, eg if you need planning permission or the weather is unsuitable.
How to appeal
If you disagree with the notice you can appeal. You have 28 days from the day after the notice was served.
Appeal in writing to the Secretary of State.
The Secretary of State for the Environment and Rural Affairs
The Planning Inspectorate
Room 4/19 Eagle Wing
Temple Quay House
2 The Square
Bristol BS1 6PN
Send a copy to your Environment Agency office at the address on the notice.
Your letter must explain why you’re appealing. Include:
- a copy of the notice
- any related correspondence
- a plan of your farm, showing the installation and any watercourses or drains
If you’re acting for a farmer on whom the notice was served, you’ll also need a statement from them confirming this.
Decisions on appeals
The notice could be:
- withdrawn or changed
- upheld, with extra time for you to comply
- upheld, with no extra time to comply - the compliance period will then usually end on the day this decision is made
These rules are based on the Water Resources (Control of Pollution) (Silage, Slurry and Agricultural Fuel Oil) (England) Regulations - known as the ‘SSAFO’ regulations - and related legislation.